An alternate system runs on the fog or great mist injected into the intake air stream. Although a number of commercial systems can be found, growers can assemble and set up their own system utilizing a high pressure piston pump and fog nozzles. The basic components are proven in Fig. 1. A two-stage system managed by a two- stage thermostat allows more water to be employed on excessively warm, shiny days. Temperature settings should be 5-10°F apart.
Algae development in the pads may become a problem that will reduce the effectiveness of the system and lead to accelerated deterioration of the pads. The addition of an algaecide to the drinking water supply can help in control.
It really is desirable, especially in hard drinking water areas, to include a wetting agent to the water to obtain additional uniform wetting of the pads. A commercial materials or liquid home detergent at the price of 2 tablespoons per 100 gallons can be used.
Water for the pads ought to be clean and lower in mineral content to avoid clogging and coating of the pads. A pump, pipes and gutters are used to recirculate the water. A flow rate 113 gallon per minute per linear foot of pad program should be provided to make sure adequate wetting.
In the most typical cooling system (fan and pad), the fans draw air through wet pads that expand the length of 1 endwall or sidewall. Aspen and covered cellulose are common pad materials that always have life of one to three years. Approximately one sq . foot of pad are is necessary for 20 square feet of floor area.
If you want to understand even more regarding Greenhouse Exhaust Fan, call us or merely see us at our site.